Forklift Fuses - A fuse comprises either a wire fuse element or a metal strip within a small cross-section that are connected to circuit conductors. These devices are normally mounted between two electrical terminals and normally the fuse is cased in a non-conducting and non-combustible housing. The fuse is arranged in series capable of carrying all the current passing through the protected circuit. The resistance of the element produces heat because of the current flow. The construction and the size of the element is empirically determined to be certain that the heat produced for a regular current does not cause the element to attain a high temperature. In instances where too high of a current flows, the element either melts directly or it rises to a higher temperature and melts a soldered joint in the fuse which opens the circuit.
If the metal conductor parts, an electric arc is formed between un-melted ends of the fuse. The arc starts to grow until the required voltage to be able to sustain the arc is in fact greater as opposed to the circuits accessible voltage. This is what results in the current flow to become terminated. Where alternating current circuits are concerned, the current naturally reverses course on each cycle. This method really enhances the speed of fuse interruption. Where current-limiting fuses are concerned, the voltage required to sustain the arc builds up fast enough in order to really stop the fault current before the first peak of the AC waveform. This effect tremendously limits damage to downstream protected devices.
The fuse is usually made from silver, aluminum, zinc, copper or alloys because these allow for stable and predictable characteristics. The fuse ideally, will carry its current for an undetermined period and melt rapidly on a small excess. It is vital that the element should not become damaged by minor harmless surges of current, and must not oxidize or change its behavior subsequent to possible years of service.
The fuse elements can be shaped to be able to increase the heating effect. In larger fuses, the current can be separated among numerous metal strips, while a dual-element fuse might have metal strips which melt immediately upon a short-circuit. This type of fuse could even have a low-melting solder joint that responds to long-term overload of low values compared to a short circuit. Fuse elements may be supported by steel or nichrome wires. This ensures that no strain is placed on the element but a spring may be integrated to be able to increase the speed of parting the element fragments.
It is normal for the fuse element to be surrounded by materials which are meant to speed the quenching of the arc. Silica sand, air and non-conducting liquids are a few examples.
Click to Download the pdf